Please help to keep this site free. If you like the info provided here for you, please click the link below and donate any amount you like. Thank you for helping!
CAUTION: Before beginning any work on receptacles, turn off the power to the circuit. For a 240-volt circuit, you may have to remove two fuses or trip a two-handed circuit breaker.
Most units have two outlets (duplex) and are rated at 15 or 20 amps, 120 volts. One or both outlets may be electrically live at all times, or one or both may be controlled by a wall switch. They may be installed in the middle or at the end of a circuit. The wiring arrangement is different in each case.
Most have three different-colored terminal screws:
A = Brass screws are hot.
B = White or silver screws are neutral.
C = Green screws are for grounding.
Receptacles may be grounding or non-grounding types. Always replace a them with a grounding type unless there's no grounding wire in the box or the box isn't grounded, then you can use a non-grounding type. To install a grounding unit to an un grounded box, you must ground the it independently. For help, consult a professional.
Because they are rated for a specific amperage and voltage, be sure to replace an old one with an exact duplicate. If your wiring is aluminum, your new one must be designed to be used with aluminum wire (look for the letters CO/ALR.) use the terminal screws only, back wiring is not suitable for aluminum wires.
Replacing Appliance Receptacles:
These are rated from 15 to 50 amps, 240 volts and from 20 to 50 amps, 120/240 bolts, each require a special plug that will fit only that particular one. Take care when replacing these because they have two hot wires, usually red and black, going to them. They may or may not have a separate grounding wire.
Replacing a Grounded Receptacle:
1. Shut off power to the circuit, un screw the cover plate and remove.
2. Unscrew the unit from its box and carefully pull it out.
3. Note which wire is connected to which terminal screw.
4. Disconnect the wires from the screws.
5. To install the new one, wrap the wires clockwise around the screws (use old the old one as a guide.)
6. Screw the new unit to the box and replace the cover plate.
Replacing a Back wired Receptacle:
1. Shut off the power.
2. Push a small-bladed screwdriver into the slots next to the wires.
3. Pull them out.
4. To install the new one push the end of the stripped black wire into the hole by the brass screws, white wire by the silver ones.
Replacing a 120/240-volt Receptacle:
1. Shut off the power and remove the receptacle from its box.
2. Label the wires and screws.
3. Detach the wires.
4. Reconnect the wires to their proper screws on the new unit.
5. Reattach the unit to the box and replace the cover plate.
Professional Hint: Using Wire Nuts:
For most simple repairs, you won't need to splice wires. But you may have to splice two or more copper wires to replace a damaged wall or ceiling light fixture or to make a connection in a receptacle, switch or junction box. To splice wires:
1. Strip 1 inch of insulation off the wires together clockwise.
2. Snip off 1/2 to 3/4 inch of the ends.
3. Cap the twisted wires with a wire nut, turning it clockwise to secure the connection.
4. Make sure the wire nut is the proper size for the wires.
CAUTION: Don't use any wire nuts to splice together a damaged extension cord.For safety, building codes allow you tosplice house wires only within junction,receptacle, fixture or switch boxes.Also, be sure to turn off the power to the circuit before you make any splice.